Australian Standard AS/NZS 5033:2021 Installation and safety requirements for photovoltaic (PV) arrays will commence in Tasmania on 1 June 2022. The Standard was published on 19 November 2021. A 6-month transition period was allowed in Tasmania to enable people to adapt to the changes.
What are the requirements for DC cables?
AS/NZS 5033:2021 clause 22.214.171.124(b) requires that photovoltaic (PV) DC cables must conform to IEC 62930 where not installed underground. IEC 62930 was published in December 2017. It supersedes the previous requirements.
What do I need to do?
Ensure the DC cables that you are installing after 1 June 2022 conform to IEC 62930. Check with your electrical wholesaler or supplier before purchasing. Compliant cables will have “62930 IEC” printed on the cable.
If you have installed DC cables which comply with the previous requirements prior to 1 June 2022 they remain compliant. If you submit a Certificate of Electrical Compliance for the installation after 1 June 2022, make sure you have records (such as photos) which show when the cabling was installed.
Compliance Guide (PDF, 128.3 KB) published May 2022.
This page has been produced and published by the Consumer Building and Occupational Services Division of the Department of Justice. Although every care has been taken in production, no responsibility is accepted for the accuracy, completeness, or relevance to the user's purpose of the information. Those using it for whatever purpose are advised to verify it with the relevant government department, local government body or other source and to obtain any appropriate professional advice. The Crown, its officers, employees and agents do not accept liability however arising, including liability for negligence, for any loss resulting from the use of or reliance upon the information and/or reliance on its availability at any time.